Bill Fisher, W4AN wrote:
> I'm in the process of making my shack remote controlled over the phone
> lines. This presents me with the challenge of how to keep the radio working
> through an electrical storm. My shack is on a very high hill and the
> tallest tower sticks up above everything for several miles. I have the
> following in place or will be in place before the station is QRV remotely:
> 1. All coax comes through an aluminum bulkhead that is grounded.
> 2. All gear is grounded to a copper bus bar with 1" strap and each side of
> the bus bar is grounded to an 8' copper ground rod.
> 3. Each tower has 3 8' ground rods on each leg of the tower.
> 4. Every antenna is fed with hardline that runs underground. On the
> tallest tower, each piece of hardline is grounded (common) at the base of
> the tower to an 8' ground rod.
> 5. Each bands antennas are controlled by at least one Ameritron RCS8V
> remote antenna switch. 10, 15, and 20 have two RCS8V's. One for switching
> the stacks and the other for selecting antennas. The switches will be
> powered off remotely when the station is not in use. When off, all
> connections are grounded I believe.
> 6. At the bulkhead I will install some kind of lightening arrestor. Any
> suggestions to brand and type?
> 7. I will install protection on each of my rotor & control cables before
> they enter the shack. So far no problems, but I'm leaving myself wide open.
> 8. High quality surge protection on AC lines & on telephone line already in
> 9. Electrical and phone lines are underground for 1500' before going above
> OK... What am I forgetting? Any suggestions?
> Bill, W4AN
> Bill Fisher, W4AN (EX KM9P)
> FAQ on WWW: http://www.contesting.com/towertalkfaq.html
> Submissions: email@example.com
> Administrative requests: towertalk-REQUEST@contesting.com
> Problems: firstname.lastname@example.org
I have no connection with, but went to their school and used the
stuff in commercial service..... Call PolyPhaser-800-325-7170. Ask for
the catalogs and then try to talk them out of their $22 book, a 95
page text on lighting and grounding.....They have bulkhead-suppressors
for HF at 3 KW.
FAQ on WWW: http://www.contesting.com/towertalkfaq.html
Administrative requests: towertalk-REQUEST@contesting.com