If you can get a quantity of heavy bare ground wire you have
another option .. install a couple of ground rods for the tower
placing them in a direction away from your house . Directly bury the
connecting cable ( # 2 bare conductor or heavier ) from these back
to the tower, Addtionaly bury a second conductor around your house
back to your service entrance point , Try to stay about a yard away
from the house and about 6 inches to a foot deep.. plant another
ground rod attached to this cable before you bring it over to your
service entrance ground.
Personaly I belive that the more metal we bury the better our station
is protected and the better our signal transmition and reception will be.
Bob Wanderer wrote:
> Eric, my tower is, for a number of reasons, adjacent to my shack, and my
> service entrance is at the diagonally opposite corner of my house. A
> 90-100 foot run around the periphery of the house would be required to
> bond the tower ground to the service entrance ground. Would that still
> be effective even if I were to spend the effort & money? Or are there
> alternatives in this case? Short of moving the tower or service
> entrance, that is!
> Chuck, N4NM<snip>
FAQ on WWW: http://www.contesting.com/towertalkfaq.html
Administrative requests: towertalk-REQUEST@contesting.com