What do you do with that "room common point" if it's
not near the service entrance ground?
> ...the SPG panel at the lower level is almost
> certainly not as necessary as the one at his shack
> entrance. The cables should all route past the
> service entrance and be grounded there, before
> coming to the shack entrance, but they do not need
> to enter the dwelling at that point through a panel.
> The feedlines can come up to the room outside in a
> nice bundle if they can't route next to telco and
> power cables to the room. He still needs a panel at
> the room entrance that connects ALL of the neutral
> conductors and acts as a room common point.
PeoplePC: It's for people. And it's just smart.