The NEC (national electric code) allows you to lay them horizontal on
top of rock if they can't be driven vertical. This is for electrical
grounding and lightning protection. I think it makes sense for RF
Hank Lonberg, P.E.,S.E. / KR7X
Lonberg Design Group Ltd.
[mailto:email@example.com] On Behalf Of Bill Gillenwater
Sent: Friday, May 23, 2003 10:35 AM
Subject: [TowerTalk] Ground Rods in Shale
Any ideas on ground rods when you have solid shale at about 3 feet down?
Have tried to drive one 8 footer so far and got about 4 feet and that
was it. I was thinking of driving one horizontal in the basement wall?
73 Bill K3SV
See: http://www.mscomputer.com for "Self Supporting Towers", "Wireless
Weather Stations", and lot's more. Call Toll Free, 1-800-333-9041 with
any questions and ask for Sherman, W2FLA.
TowerTalk mailing list