|Subject:||Re: [TowerTalk] Noise|
|From:||Greg Gobleman <email@example.com>|
|Date:||Fri, 05 Nov 2004 18:15:14 -0600|
I had a guy wire on a power pole which was very close to the support
cable for the cable TV. Not sure what the power company may have had
attached to the guy wire, as a possible ground, or.... Anyway, every
time the wind was easterly, it pushed the pole just enough to arc
between those two and I had terrible noise. |
I was running around with a little AM radio and gave that guy wire a shaking and discovered that is what it was. As it swayed it arced. Power company put a big rubber wrap around insulator on it and I had no problem after that.
Interesting that everything in the neighborhood radiated that noise. Fences, lines, guys. For several blocks around, when the source was in front of my house.
73 Greg K9ZM
See: http://www.mscomputer.com for "Self Supporting Towers", "Wireless Weather Stations", and lot's more. Call Toll Free, 1-800-333-9041 with any questions and ask for Sherman, W2FLA.
_______________________________________________ TowerTalk mailing list TowerTalk@contesting.com http://lists.contesting.com/mailman/listinfo/towertalk
|<Prev in Thread]||Current Thread||[Next in Thread>|