> Maybe I have misunderstood what I have read about the
> Code, but your suggestion about having a ground bus
connected to the
> *neutral* sounds like a violation because it could
> connection between the neutral and the ground (if you
connect to this
> "neutral bus" a device that has a ground connection via
the green wire
> in the power cord) other than at the service entrance
> means at or close to the meter).
No, I misspoke.
I should have said safety ground, not neutral. The neutral
should only be grounded at the service panel.
See: http://www.mscomputer.com for "Self Supporting Towers", "Wireless Weather
Stations", and lot's more. Call Toll Free, 1-800-333-9041 with any questions
and ask for Sherman, W2FLA.
TowerTalk mailing list