|Subject:||Re: [TowerTalk] RE: TowerTalk Digest, Vol 25, Issue 139|
|From:||Gary Schafer <email@example.com>|
|Date:||Mon, 24 Jan 2005 21:49:04 -0500|
Why do you think the wire rating should be any different than in the house?|
Wire size should be rated for the full amount of the breaker. A 15 amp breaker will not trip at 15 amps immediately. It takes several minutes. Some it takes almost twice that to ever trip them.
An electric water heater is a pretty constant load.
73 Gary K4FMX
Keith Dutson wrote:
Barn wiring is pretty simple. Your wire needs to be rated at a bit above half the breaker amperage to handle the anticipated constant amperage. Max current only happens when lights are first turned on and motors/fans start. It's not like a house where you would be running several appliances at one time.
See: http://www.mscomputer.com for "Self Supporting Towers", "Wireless Weather Stations", and lot's more. Call Toll Free, 1-800-333-9041 with any questions and ask for Sherman, W2FLA.
_______________________________________________ TowerTalk mailing list TowerTalk@contesting.com http://lists.contesting.com/mailman/listinfo/towertalk
|<Prev in Thread]||Current Thread||[Next in Thread>|
|Previous by Date:||Re: [TowerTalk] Trees, Mountains, 15 degrees..., Pete Smith|
|Next by Date:||Re: [TowerTalk] Shack wiring, Gary Schafer|
|Previous by Thread:||RE: [TowerTalk] RE: TowerTalk Digest, Vol 25, Issue 139, Keith Dutson|
|Next by Thread:||RE: [TowerTalk] RE: TowerTalk Digest, Vol 25, Issue 139, Keith Dutson|
|Indexes:||[Date] [Thread] [Top] [All Lists]|