All this grounding talk has got me thinking again.
Most of us know that the impedance of a wire is increased by its skin
resistance, and that a wire with more skin area (such as a strap) will
provide a lower impedance. But how much lower? I decided to break out my
spread sheet I made for calculating these things and take a look. The
data is tabulated below.
Some interesting conclusions can be drawn from this data. For example,
at 330 HZ the impedance of a #4 wire due to its inductance is the same
as its skin resistance, but the DC resistance still dominates. At 1660
Hz the impedance due to inductance is equal to the total DC resistance
(skin plus DC resistance). That means for any frequency above 1660 Hz,
the impedance of the wire is due primarily to its inductance, not its DC
resistance or skin resistance. As a matter of fact, above about 20 KHz,
the DC resistance and skin resistances are insignificant for this wire,
even though they are continually increasing. Since all these parameters
are linear with length, this conclusion is the same regardless of the
length of the wire. For a #2 wire, this same point happens at 1100 HZ
instead of 1660 Hz.
Note that when applying these conclusions to other things besides ground
wires, there is a difference between impedance due to inductance and
impedance due to resistance.

Calculated data:
#4 wire, 10 ft length, L = 0.43 uH (straight wire in free space)
Note: A wire in the ground will appear as a higher inductance than shown
here, because of the decreased velocity factor of the medium.
Z(L) represents impedance calculated from inductance only.
Freq Z(L) DC res Skin res
330 Hz 8.86e4 2.49e3 8.86e4
920 Hz 2.47e3 2.49e3 1.48e3
1660 Hz 4.46e3 2.49e3 1.99e3
10 kHz 2.69e2 2.49e3 4.88e3
100 kHz 0.269 2.49e3 1.54e2
1 MHz 2.69 2.49e3 4.88e2
I didn't have a spreadsheet already made up to calculate the skin
resistance of a strap, but I do have one to calculate its inductance.
Since the inductance is the predominate parameter, it's probable all you
will need anyway. The calculations are for a strap thickness of 0.05
inches, and a length of 10 ft. Since the thickness doesn't effect the
inductance very much, it wasn't included as a variable parameter.
Compare these numbers to a #4 wire, same length, which was 0.43 uH.
Strap width Inductance uH
0.5 in 0.40
1 in 0.36
2 in 0.32
3 in 0.30
4 in 0.28
5 in 0.27
6 in 0.26
The formula for the wire inductance and strap inductance came from the
Polyphaser book, Grounds for Lightning & EMP Protection.
One other note of significance: None of these calculations include
resonant effects. For wires that are long compared to the frequencies
being considered, resonance effects can increase the impedance by a huge
amount compared to an impedance value calculated from wire inductance.
Jerry, K4SAV
_______________________________________________
_______________________________________________
TowerTalk mailing list
TowerTalk@contesting.com
http://lists.contesting.com/mailman/listinfo/towertalk
