Phil Camera wrote:
> Nope, per NEC, #6 or larger. I use #4 bare solid. Don't go cheap now;
> do it right.
NEC doesn't say it has to be a single conductor. Yes, your local
inspector might look askance, but if you can make a convincing case that
the cross sectional area of your 3 AWG8 conductors in parallel is
greater than a AWG 6 (which it is), then you're good to go.
TowerTalk mailing list