> "Strip B into Strip A, and Strip C into Strip B..."
In the U.S., UL Standard 1363 prohibits the cascading of relocatable power
taps (i.e., "portable outlet strips"). Many municipal ordinances
incorporate Standard 1363 into their local codes. Outside of a brief
mention in Article 220 regarding multi-outlet assemblies, I don't believe
the NEC directly addresses the use of relocatable power taps since the NEC
is designed as an installation standard, and not a product standard, like
TowerTalk mailing list