Towertalk
[Top] [All Lists]

## Re: [TowerTalk] Resistance in house neutral

 To: "Tower Talk List" Re: [TowerTalk] Resistance in house neutral "Jim Brown" Mon, 26 Jul 2010 09:57:58 -0700 mailto:towertalk@contesting.com>
 ```On Mon, 26 Jul 2010 11:19:53 -0400, Pete Smith wrote: >I just measured the resistance between the neutral wire on one outlet in >my shack and the SPG entry panel, which is grounded through 35 feet of >#2 wire to the same ground stake used by the breaker panel. To my >surprise, it measured (DC) 88 ohms. Isn't that far too high? I expect >I have some trouble-shooting to do. Maybe, or maybe not. I suggest that you make a simple spreadsheet for the expected resistance based on the length of wire from outlet to panel, from panel to the ground rod(s), and your shack to the ground rods. Assume #14 for 15A circuits, #12 for 20A circuits. #12 is 1.588 ohms/1,000 ft, #14 is 2.525 ohms/1,000 ft. #2 is 0.156 ohms/1,000. The ONLY connection between neutral and ground must be at the breaker panel where power comes into the house, and it must be a VERY good bond. One thing that could muddy the water is the presence of current on those conductors, which is highly distorted. Distortion can also result in imbalance -- that is, DC -- and that DC could be giving you a false resistance reading. I would look into that before chasing your tail too far. :) To get rid of that distortion, you'll need to kill power to the building. One good way to get at least a rough handle on proper bonding is to look at the AC voltage between neutral and ground with a meter that reads low AC voltages well. The only place it should be zero is at the panel, or very close to the panel (in terms of wire length). Anything up to a volt or so is normal at outlets that are drawing current. The voltage is mostly the result of IR drop on the neutral, but can also be caused by leakage currents. In a steel structure with other big power draws, the leakage currents can be significant (a volt or more). If you see zero volts at an outlet with something plugged into it, there's probably a bonded neutral in that equipment. Don't rule out mis-wired outlets. They get wired by humans, so the law of averages says that almost every building will have at least one, and that's all it takes to make a mess. A simple outlet tester is a great investment. Ecos and Tasco are the best brands, but hard to find. Ideal also makes one that is less useful. 73, Jim Brown K9YC _______________________________________________ _______________________________________________ TowerTalk mailing list TowerTalk@contesting.com http://lists.contesting.com/mailman/listinfo/towertalk ```
 Current Thread [TowerTalk] Resistance in house neutral, Pete Smith Re: [TowerTalk] Resistance in house neutral, Kipton Moravec Re: [TowerTalk] Resistance in house neutral, Jim Brown <= Re: [TowerTalk] Resistance in house neutral, Pete Smith Re: [TowerTalk] Resistance in house neutral, Jim Brown Re: [TowerTalk] Resistance in house neutral, jimlux [TowerTalk] Plumbing a Towerl, Mark Robinson Re: [TowerTalk] Resistance in house neutral, Pete Smith