Towertalk
[Top] [All Lists]

## [TowerTalk] Fwd: shack wiring

 To: [TowerTalk] Fwd: shack wiring "Jim Thomson" Mon, 2 Aug 2010 04:16:50 -0700 mailto:towertalk@contesting.com>
 ```Date: Sun, 01 Aug 2010 09:56:23 -0700 From: "Jim Brown" Subject: Re: [TowerTalk] Fwd: shack wiring In a 3-phase system, any harmonic whose number is divisible by three will ADD in the neutral rather than cancel. That's because the three phases are displaced by 120 degrees at the fundamental, and their third harmonic is displaced by 3x120 degrees (360 degrees). Likewise, the sixth is displaced by 720 degrees, the 9th by 1080 degrees, etc. Those harmonics add in the neutral (AND in leakage currents on ground conductors). And it is those harmonics that we hear as "ground buzz." Now, almost none of us has 3-phase at home, but the mains power wiring in the alley or underground that feeds us IS 3-phase, and a form of 3-phase power distribution called High Leg Delta is widely used in cities, towns, and even some rural areas to feed both residences and businesses from the same lines. A center-tapped transformer on one of the phases feeds residences, while businesses that need 3-phase power get all three phases (but no neutral). The catch is that residences DO get a neutral, and all that harmonic noise from the businesses goes to ground on our neutral. If you hear "ground buzz", that's what you're listening to! ## If the business's don't get a neutral... then how do the business's obtain 120 vac ?? The usual deal with 208/120 3 phase is... Phase to neutral = 120 vac IE: 208/sqrt 3 Perhaps the business's are all stuck with 208 vac single + 3 phase?? ## I read a while back abt hi tech business's.. that huge hundreds of 120 vac PC's... were really cooking the 600v primary /208-120 sec distribution xfmr..located on each floor of a 4 story building. The 600 vac was fed to the riser. The problem with all the 120 vac loads was the harmonics. The neutral current was double normal.. and sometimes more than double normal. ## each floor had a 50 kva xfmr... and the average load was 37 kva. The 50 kva xfmr was ready to burn up... and the hvac in eacg xfmr room on each floor...was running flat out. The 'fix' was to use these new type xfmrs... amphorous with a 3rd winding em. They killed the harmonics.. and the new style 50 kva xfmr doesn't heat up. The original solution was to replace the xfmr with a 75/100 kva conventional unit. ## the power up here is always on abt harmonics. Those silly CF lights have real lousy power factor .48 The kicker is.. in zl/vk land... they have perfect pf. The ones from both zl/vk and NA..come out of the same factory... in china ! The ones soild here are missing the small choke..used to cancel the XC from the leading PF of the CF lights...go figure. ## some power co's in the usa were abt to penalize folks for lousy pf... but of course that got squashed. CF's are all the rage...even with .48 pf All they have to do is add the choke back in. You can see where it goes on the pc board inside em. There is a jumper across the 2 x holes in na models. ## bottom line is... big city sucks 480 kw worth of CF lights... but the power co has to provide 1 million VA to do it. ## In EU.. any power supply > 75 watts has to have PF correction built into it plus harmonics have to be suppressed. I stopped by the telco where I just retired from.... and noticed they had changed out all the old style Ferro resonant 400A rectifiers with these new tiny switching types. the new ones have almost unity PF. [ >.99] To pull that off, they have improved the pf.. plus killed all the harmonics. New ones are tiny things.... 6 will easily fit into a 24" wide rack 6" tall x 15" deep]. heat sinks never get hotter than 102 deg F. Old style units would cook a room. Later... Jim VE7RF If you can look at the buzz on an audio spectrum analyzer, you'll see those harmonics. I've got screen shots an FFT analyzer and an extended discussion of all of this in a couple of tutorials that are on my website. See either the Ham Interfacing tutorial or the White Paper on Power and Grounding for Audio and Video Systems. http://audiosystemsgroup.com/publish.htm 73, Jim Brown K9YC _______________________________________________ _______________________________________________ TowerTalk mailing list TowerTalk@contesting.com http://lists.contesting.com/mailman/listinfo/towertalk ```
 Current Thread [TowerTalk] Fwd: shack wiring, hanslg Re: [TowerTalk] Fwd: shack wiring, Jim Brown [TowerTalk] Fwd: shack wiring, Jim Thomson <= Re: [TowerTalk] Fwd: shack wiring, Paul Christensen Re: [TowerTalk] Fwd: shack wiring, TexasRF Re: [TowerTalk] Fwd: shack wiring, Paul Christensen Re: [TowerTalk] Fwd: shack wiring, TexasRF Re: [TowerTalk] Fwd: shack wiring, Charlie Gallo [TowerTalk] Fwd: shack wiring, Jim Thomson Re: [TowerTalk] Fwd: shack wiring, Joe Subich, W4TV [TowerTalk] Power Distribution, Jim Brown Re: [TowerTalk] Fwd: shack wiring, Paul Christensen Re: [TowerTalk] Fwd: shack wiring, Grant Saviers