[RFI] 80/160M RFI in neighbor's oven circuitry (PART 2)
RFI Services' Mike Martin
mike at rfiservices.com
Sun Feb 8 13:41:19 EST 2009
I think the ground socket is now required to be installed on top so if a
conductive cover plate were to come loose it will fall onto the ground
terminal instead of shorting the hot leg to the neutral.
Sometimes this creates issues with the way a heavy duty cord is molded and
are too short to work.
6469 Old Solomons Island Rd
Tracys Landing, Md 20779
More information about the RFI