Your white neutral had better be connected to the ground at the service
panel ... that is the correct practice here in NA.
I'll run the race and I will never be the same again.
From: email@example.com [mailto:firstname.lastname@example.org]
On Behalf Of email@example.com
Sent: October 29, 2009 9:24 AM
To: Robert Groh; firstname.lastname@example.org; email@example.com
Subject: Re: [Amps] TL922 Power Plugs
In fact in my house all the Neutral wires are connected to the gnd bus
bar at the service panel
Amps mailing list