Gary Smith wrote:
> And in California. I would check that out. You may got a short (!) trip you
> might not want.
Houses are typically feed off of a center tapped secondary. 240V
measured between phase conductors and 120V between either phase
conductor and the center tap. There isn't any sort of dangerous short
by having the neutral ( i.e. center tap) and the ground bonded together
in the primary distribution panel in a house....its supposed to be
connected that way.
Amps mailing list