|Subject:||Re: [RFI] PME (Was: Earth isolation)|
|From:||"Ian White, G3SEK" <G3SEK@ifwtech.co.uk>|
|Reply-to:||"Ian White, G3SEK" <firstname.lastname@example.org>|
|Date:||Mon, 20 Sep 2004 10:12:23 +0100|
George Shaw wrote:
There are several different problems here.
First, what kind of "radio operator" do you have, next door? Licensed, or not? What frequency, what power?
Second, you say your own equipment is "near quiet"... so it's not totally immune to your own transmissions? Again, you need to give a lot more detail before anyone here can really help.
Now another question. Any thoughts or comments/data on Protective Multiple Earthing systems and interference or use near/in radio installations?For information, PME is a British system by which the electricity supplier takes over responsibility for safety grounding, by multiple grounding of the neutral supply line. The claimed advantage is that users don't have to rely on the quality of grounding at each individual house.
Inside the house, all accessible metalwork has to be bonded to the common earth bus, which is connected to the grounded neutral. This makes a safe "equipotential zone" inside the house... but it isn't necessarily the same potential is the ground on which the house is built. When you connect *anything* out of the house to the real world outside, the whole concept comes unglued.
From the specific viewpoint of RFI, George and his "radio operator" neighbor may be sharing a common ground/neutral lead, which may go several yards back up the supply system before it finds an earth spike.
Personally I hate, loathe, detest and despise PME! If I ever move to a house that has PME (a distinct possibility in the next 12 months), the first thing I'll do is change it, and provide my own earth connection that is short and direct.
As far as I know, there is no objection to George installing a good ground of his own, with the shortest possible lead-in to the earth busbar in the "consumer unit" (breaker panel). That could be a big help with the RFI... but there are detailed regulations about the size of wire and earth spike required. Consult the 'IEE On-Site Guide.'
Also anyone ever had a electricity supply board timer (used to change for daytime high rate to evening/night time low rate) cause interference to radio or telephone circuits by introducing a click, click, click steady repeated sound?Sorry, no info on that.
|<Prev in Thread]||Current Thread||[Next in Thread>|
|Previous by Date:||RE: [RFI] PME (Was: Earth isolation), George Shaw|
|Next by Date:||[RFI] ARINC's summary of BPL modeling & interferenceanalysis, ERIC ROSENBERG|
|Previous by Thread:||[RFI] PME (Was: Earth isolation), George Shaw|
|Next by Thread:||[RFI] 40 meter intruder?, Cortland Richmond|
|Indexes:||[Date] [Thread] [Top] [All Lists]|