[TenTec] Re. [Ten Tec] Grounds
tvman1954 at gmail.com
Tue Jan 24 17:30:38 PST 2012
Am I grounded O.K.
We live in a Triplex and I have an apartment on each side . All of the
Hot/Cold water pipes which are 1/2" copper are buried under the concrete
slab at about 18" down. Of course the Hot water pipes are insulated, so I
am sure they make for an high impedance/resistance to earth, if any at all
except for any connection to the cold water pipes at the 3 water heaters
recpectively. My station ground consists of a copper strip about 4" wide
and 4' long which every piece of equipment is well bonded to. The ground
wire is #2 stranded copper less than 5 feet long connected directly to the
water pipes. From the water pipes another piece of #2 stranded copper wire
less than 3 feet long runs through the brick wall to the electrical service
ground which I have beefed up by adding another 10 foot copper clad ground
rod. Also, bonded to the Cable TV ground rod in same manner about 6 feet
................ So, have I done it correctly? .............. My HF
antenna is a flat top dipole at around 40 feet and fed with 450 ohm Ladder
Line. What I can tell everyone is that IF, we unhook the ground system at
40 meters or 160 meters there is so much RF on my signal that it makes it
very hard for folks to copy my station. On 75/80 meters I can get by until
the Amplifier comes online. With the grounds we are Fine Business.
Yes, Airplanes, Space Shuttle/Station, Rockets and Hot Air Balloons may
transmit without grounds but, in my experience MY station works better and
I have much less noise with the station grounded,
73 de Wade/KJ4WS
On Tue, Jan 24, 2012 at 6:15 PM, John <jh.graves at verizon.net> wrote:
> My house sits on directly on ledge and I have the rocks in the basement
> area to prove it. Headspace goes from 7 ft in the back corner where my
> furnace is to about 3 ft in the front of the house. The outside
> perimeter sits on exposed ledge for about 90 percent of the perimeter
> distance. The ledge extends out for 3 ft or better although parts of
> the ledge may have 2-5 inches of earth cover. So do I drill an hole in
> the ledge and drive some more rebar in to make my rf ground? Praying
> has also come to mind and for 40 odd years it seems to have worked?
> John / WA1JG
> On 1/24/2012 3:47 PM, Stuart Rohre wrote:
> > Technically, a ground wire covered by the deck is a violation of the
> > National Electrical Code. Likely the rod was there first, and the deck
> > was built over it.
> > Breaker boxes, switched disconnects, panel boards and ground rods must
> > be accessible for inspection and repair. It is common for ground rod
> > connections to get disturbed by ground shifting, hit by grounds keeping
> > equipment, etc. and thus require the clamp to be tightened over time.
> > The typical house or ham ground rod does little to improve your RF
> > performance, as the inductance of the long lead between the shack ground
> > bus and the electrical entry ground rod will often mean you have a
> > quarter wave situation at the high bands, ie high impedance at one end
> > where your rig connects.
> > Better to put a buried halo ground around the house outside the
> > foundation, and connect, (bond) both electrical grounds and the
> > communications grounds, as well as ham radio ground to it.
> > That way, you have provided a physically short path to earth from any
> > place in the house where the shack might be.
> > Be aware however, everything bonded together, with the case of a less
> > than good conducting earth, that you could have a hit on an antenna mast
> > or tower, bonded to the common bus. The whole of the bonded system will
> > rise to a very high potential, and might conduct harmful currents into
> > equipment bonded to everything else. We had this happen at the club
> > station: tower was hit, current came in on shields of coax, (coax was
> > INSIDE the tower), and continued into the shack where it went around the
> > room on our bus bar, up into a VHF radio, and vaporized the circuit
> > board negative power trace before arcing through the power supply to the
> > AC third pin ground path back to the AC utility ground.
> > The ground bus was L shaped around two sides of the room and on the
> > short side went out to a metal water supply piping system. Everything
> > was bonded to it with wide flat conductors, thus low inductance.
> > All AC outlets were bonded by the AC wiring (3 wire plus conduit).
> > Sometimes it is just going to get you if equipment is left plugged in.
> > Stuart Rohre
> > K5KVH
> > _______________________________________________
> > TenTec mailing list
> > TenTec at contesting.com
> > http://lists.contesting.com/mailman/listinfo/tentec
> TenTec mailing list
> TenTec at contesting.com
More information about the TenTec